View Full Building Record as of 05/05/2020 (PDF)
2017/08/17 Failed. Conservation annual inspection #11700502 related to complaints.
See details below.
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN190019||Arrange for inspection of premises. (13-12-100)||Interior of building-no response, unverified detectors-no entry,unable to verify complaint of apartment 109-no heat.|
|CN190019||Arrange for inspection of premises. (13-12-100)||No entry to most areas and apartments,unverified detectors,conditions.|
|NC5012||Failed to provide stairwell opening with self-closing, framed, 1-1/2 hour Class B door. (15-8-180)||East elevation / interior stairwell doors-not fire rated.West and east stairwell doors-held open with wedges.|
Photos Submitted by Users
Reviews of Building
0 out of 5 stars (based on 0 reviews)