2018/09/28 Failed. Conservation annual inspection #11255726, possibly related to complaints.
See details below.
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN031023||Failed to maintain properly charged fire extinguisher and to attach tag which clearly indicates recharge date and signature of the person who performed the recharge. (15-16-680)||Basement – fire extinguisher – Out dated.|
|CN107015||Failed to provide and maintain adequate illumination for public hall and stairwell. (13-196-080, 13-196-450, 13-160-660, 13-160-670)||Basement – emergency lights – Out of service.|
|CN190029||pending notice reinspection||Gained entry to basement and all three common hallway’s but to any units to verify Detectors. Unverified complaint of broken carbon monoxide detector in unit #6.|
|CN196029||Post name, address, and telephone of owner, owner’s agent for managing, controlling or collecting rents, and any other person managing or controlling building conspicuously where accessible or visible to public way. (13-12-030)||No owner’s i.d sign posted.|
Photos Submitted by Users