Currently under investigation.
View Full Building Record as of 05/05/2020 (PDF)
2016/02/26 Failed. Conservation annual inspection #10933790.
See details below.
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN065014||Failed to maintain lintel in good repair and free from cracks and defects. (13-196-530(e), 13-196-641)||West elevation, Lintels – 3rd and 4th floors – Rusted.|
|CN197079||Repair or replace defective or out of service smoke detectors and operate continuously. (13-196-130, 13-196-140)||1st floor laundry room – Smoke detector out of service.|
|CN198019||File building registration statement with Building Dept. (13-10-030, 13-10-040)||Building not registered for 2016.|
|EL0027||Restore exit and emergency lighting system and related equipment to operable condition. (18-27-700.6)||All floors missing emergency lighting in corridors and stairwells.|
|NC5062||Failed to remove fusible links and/or other hold-open mechanism on stairwell doors in buildings where stairwells serve more than three floors. (15-8-180(c))||All floors – stairwell doors being held open without a fail-safe device.|
Photos Submitted by Users
Reviews of Building
0 out of 5 stars (based on 0 reviews)