2019/09/03 Failed. Conservation annual inspection #10621294.
See details below.
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN061014||Failed to maintain the exterior walls of a building or structure free from holes, breaks, loose or rotting boards or timbers and any other conditions which might admit rain or dampness to the walls. (13-196-530(b), 13-196-641)||East elevation /exterior wall – spalled bricks, with washed out mortar.|
|CN063014||Failed to maintain chimney in safe and sound working condition. (13-196-590, 13-196-530(b) and (c), 13-196-641)||Chimney – stepfractured bricks, with washed out mortar. Chimney capping has missing tile sections.|
|CN070024||Failed to repair or replace defective or missing members of porch system. (13-196-570, 13-196-641)||East elevation /open wood porch – 1st floor decking boards – rotting sections.|
|CN190029||pending notice reinspection||Interior of building /no response. Unverified occupancy, detectors, and conditions. Unable to inspect interior stairway systems and basement.|
Pictures Submitted by Users
Reviews of Building
0 out of 5 stars (based on 0 reviews)