Still under investigation.
View the full building record as of 05/06/2020 (PDF)
2018/10/10 Failed. Conservation annual inspection #11605999.
See details below.
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN063014||Failed to maintain chimney in safe and sound working condition. (13-196-590, 13-196-530(b) and (c), 13-196-641)||West elevation – chimney – spalling bricks and washed out mortar near top.|
|CN190029||pending notice reinspection||Gained entry to all common hallway’s and only unit 203 but to all other units and boiler room to verify Detectors.|
Photos Submitted by Users
Reviews of Building
0 out of 5 stars (based on 0 reviews)